- Pumped 530,250
- Backwashes 50,220
- Net pumped 480,030
- Source meter 318,140
- Flushing 6,000
- Net to distribution 312,140
- Residential meters 212,140
- Unaccounted for water 100,000
- Percentage of loss 32%
Kevin attended the ERWOW conference in Yakima in February.
I am still working on the turbidity levels in the treatment plant. Last year we had heavy rain in the spring and it took into mid summer before we got control of the turbidity levels. I took several samples, discussed the results with the engineers at the Department of Health, and technical support at ERWOW. This is now an ongoing problem. It clearly is not the reservoir, and I have tried numerous approaches all to no avail.
We are completing as much cleanup on the docks as possible. We should have all of our part of the work done this week.
We pressure washed the steps to the clubhouse and cleaned the clubhouse roof as best we could. The roof and decking needs a full cleaning this summer.
I will be attending the WOW conference in March.